by William Harmon
(Charleston, SC, USA)
I apologize for the long story but am perplexed.
Summer of 2012 heat would be produced when thermostat was set for cooling. I was able to get a new defrost board under wty. That did not fix my problem. I learned power has to be applied to reversing valve for cooling to take effect. To determine if reversing valve was good or not, I removed the black wire from the def brd that ran to the rvsg valve and jumped power from the little 24V circuir breaker to the rvsg valve. It clicked. So I left the jumper in place. AC worked. Left jumper in all summer and AC worked fine.
Winter 2012 came.... I pulled the jumper out. Placed wire back into def brd. Heat worked fine and defrost cycle ran all winter.
Summer 2013 came.... I put jumper back in... AC worked fine all summer. I know it wasn't good to keep pwr applied to the valve all the time but.... didn't seem to hurt.
Now... winter 2013. I pulled jumper out. Placed wire back into def brd..... heats fine but we had our first cold night (low 30s) and the def mode did not kick in.... condenser a block of ice all the way around.
Manually defrosted... heat works fine and we will have nights in the 40s and 50s for the next week or so, so we'll be fine until it gets into the low 30s or below.
I also swapped the digital thermostat with the same model. Made sure all settings were the same. No difference. Also checked all 24V wiring and connections. Some spliced connections were questionable, so I stripped and reconnected.
With the def brd already replaced and the rvsg valve known to be good. Any ideas where to look now?
Payne (Carrier)model PH3PNA048000AA
Def Board PN HK32EA003
Thanks in advance for any ideas.
Comments for No Cooling or Defrost Mode
Click here to add your own comments
Join in and write your own page! It's easy to do. How? Simply click here to return to Heat Pump Problems.